|Place of Origin:||China|
|Brand Name:||New Light|
|Minimum Order Quantity:||10 pcs|
|Packaging Details:||1 piece per pack|
|Delivery Time:||within 2 weeks|
|Payment Terms:||T/T, Western Union, MoneyGram|
|Supply Ability:||1000 pcs per month|
|Color:||Green||Name:||MTP Trunk Cable|
mpo to mpo cable,
mpo fanout cable
MPO-MPO 12Cores 3M OM3 multimode Fiber optic patch cord cable MPO-MPO Indoor pre - terminated Fiber optic cable
Jacketed cable is compliant with NFPA 262 Optical Fiber Nonconductive Plenum (OFNP) or IEC-60332 Low Smoke Zero Halogen (LSZH) flame rating.
Compliant to Directive 2002/95/EC (RoHS) and REACH SvHC.
MPO connector complies with IEC-61754-7 &amp; EIA/TIA-604-5.
Connector End face: MPO end face geometry requirements: EN50377-15-1
Polishing Quality:: Polished end-face quality: IEC61300-3-35
Our MPO patch cables are designed for data center solutions supporting the topologies such as 10
Gigabit Ethernet, Fiber Channel or Infiniband - as specified in the data center standards EN50173-5 and
Optimized Performance- Assemblies constructed with low loss MPO/MTP OECE proprietary MT polishing Provides low insertion loss and high return loss, minimizing variability for improved channel link loss performance.
MPO patch cables are used to make the interconnections between the MPO cassettes or connections to active equipment with MPO/MTP interface.
In cases where an MPO patch cord is connected (through an MPO coupler) to another MPO patch cable, one of the two MPO connectors must be male (equipped with pins).
MPO patch cables are available in 3 different wire map configurations: Straight, Total Flipped or Pair Flipped
MPO patch cables are available in multi-mode and single-mode fiber cable.
Performance of Assemblies MTP / MPO Termination:
|Type/Performance||Singlemode(APC polish)||Multimode(PC / Flat Polish)|
|Standard||Elite Low Loss||Standard||Elite Low Loss|
|Maximum Insertion Loss||≤ 0.75dB||≤ 0.35dB||≤ 0.60dB||≤ 0.35dB|
|Return Loss||≥ 50dB||N/A|
|Operating Temperature||-40°C to 80°C||40°C to 80°C|
Contact Person: Mr. Michael